Checking for non-preferred file/folder path names (may take a long time depending on the number of files/folders) ...
This resource contains some files/folders that have non-preferred characters in their name. Show non-conforming files/folders.
This resource contains content types with files that need to be updated to match with metadata changes. Show content type files that need updating.
Feasibility of Locating Leakages in Sewage Pressure Pipes Using the Distributed Temperature Sensing Technology
|This resource does not have an owner who is an active HydroShare user. Contact CUAHSI (firstname.lastname@example.org) for information on this resource.
|The size of this resource is 1.0 MB
|Dec 29, 2017 at 10:32 p.m.
|Apr 09, 2018 at 8:51 p.m.
|See how to cite this resource
|Be the first one to this.
|No comments (yet)
The cost effective maintenance of underwater pressure pipes for sewage disposal in Austria requires the detection and localization of leakages. Extrusion of wastewater in lakes can heavily influence the water and bathing quality of surrounding waters. The Distributed Temperature Sensing (DTS) technology is a widely used technique for oil and gas pipeline leakage detection. While in pipeline leakage detection, fiber optic cables are installed permanently at the outside or within the protective sheathing of the pipe; this paper aims at testing the feasibility of detecting leakages with temporary introduced fiber optic cable inside the pipe. The detection and localization were tested in a laboratory experiment. The intrusion of water from leakages into the pipe, producing a local temperature drop, served as indicator for leakages. Measurements were taken under varying measurement conditions, including the number of leakages as well as the positioning of the fiber optic cable. Experiments showed that leakages could be detected accurately with the proposed methodology, when measuring resolution, temperature gradient and measurement time were properly selected. Despite the successful application of DTS for leakage detection in this lab environment, challenges in real system applications may arise from temperature gradients within the pipe system over longer distances and the placement of the cable into the real pipe system.
Raw project data is available by contacting email@example.com
How to Cite
This resource is shared under the Creative Commons Attribution CC BY.http://creativecommons.org/licenses/by/4.0/